EasyPower Expert Services
Click a section below to read details of our expert service offerings.
Contact us to learn more about EasyPower Expert Services, get a quote, or talk to an engineer about your project.
Contact Us - Expert Services
Arc Flash Risk Assessment
EasyPower's expert engineering staff can provide complete turnkey arc flash risk assessment, or support your team through any part of the process. Using EasyPower®, we can provide a variety of services to meet your arc flash needs:
- Show the step-by-step process to compliance
- Evaluate the needs of your facilities for arc flash risk assessment
- Provide implementation support
- Review software needs, application training requirements
- Define the amount of engineering services required for your facilities’ compliance
- Evaluate various electrical system configurations and operating modes
- Determine arc flash protection boundaries
- Develop proper PPE requirements, work procedures, warning labels, and floor stripes
- Identify ways to manage PPE requirements, while avoiding costly productivity losses and safety risks due to over-specification of PPE
- Print high quality, weather-resistant vinyl warning labels
Our staff engineers can visit the site, gather information, perform the analysis, and if desired, train plant engineers and electricians to help ensure ongoing compliance.
Our system study report includes the results of the EasyPower® analysis, recommendations, and a prioritized action plan. This report is provided to help ensure proper electrical equipment ratings and settings, PPE selection and electrical service reliability.
Contact us to learn more about EasyPower arc flash studies.
Short Circuit Analysis
Short circuit calculations are required to correctly apply equipment in accordance with NEC and ANSI standards. Depending on the size and utility connection, the amount of detail required to perform these calculations can vary greatly. EasyPower’s short circuit analysis will include calculations performed in accordance with the latest ANSI standards.
Switches, fuses, and breakers that need to interrupt or close into a fault are of special concern. Cables and buswork also have short circuit withstand limitations, and a thorough study will examine non-interrupting equipment, as well as switches and breakers. Standards such as ANSI C37.010 and C37.13 outline the recognized calculation methods for these equipment-rating analyses.
Short circuit calculations are required for the application and coordination of protective relays and the rating of equipment. All fault types can be simulated. EasyPower’s short circuit study provides a detailed report identifying breaker ratings, breaker fault duties, discussions, and recommendations for any deficiencies found.
Contact us to learn more about EasyPower short circuit studies.
Power Flow Analysis
EasyPower’s power flow analysis utilizes a computer model to examine normal steady state and contingency conditions in an electrical system. A power flow solution provides voltages and equipment loadings under a given set of system conditions. A series of power flow cases can show the effects of various design alternatives or equipment outages on system operation.
An engineer can use power flow cases to:
- Examine benefits of load-tap-changing transformers
- Examine benefits of power factor correction capacitors
- Select locations for power factor correction capacitors
- Set taps on fixed-tap transformers
- Explore steady state performance of expansion alternatives
- Determine ratings for new or upgraded circuits
- Determine equipment loading
In addition, a power flow case can provide a snapshot of system voltages during motor starting, impact loading, or other short-term events that affect system voltages.
Contact us to learn more about EasyPower power-flow studies.
Power Factor Analysis
Power factor improvement is a cost-effective method to meet the reactive demand of a plant or distribution system. Power factor improvement may be warranted simply from the benefits it provides in voltage increase and reduced loading of transformers, cables, and generators.
The technical and economic value of power factor improvement is verified through an analysis of the plant electrical system and loads. Also, planning for present and future kVAR needs may require additional studies. If harmonics are present, the selection of capacitors will be more complex and the location more critical. Frequent switching of capacitors can cause transient over-voltages, and isolated motors on capacitors may have to be examined for self-excitation.
EasyPower® PowerFlow serves as an excellent tool to evaluate power factor improvement alternatives. Using PowerFlow, EasyPower engineers can provide power flow analysis to reveal actual power factor correction, while providing analysis of potential problem areas. Excessive voltage regulation may indicate a need for including automatic voltage control equipment.
Contact us to learn more about EasyPower power factor studies.
Motor Starting Analysis
EasyPower’s motor starting analysis identifies the expected voltage dip and acceleration time for a motor and the effects of motor starting on a system. Alternate starting methods, such as across-the-line, reactor, capacitor, or autotransformer start, can be explored.
If system voltage dips are a concern, EasyPower engineers will propose the appropriate solutions. For calculating acceleration times, they will employ advanced, dynamic simulation with inertia and other machine data.
Contact us to learn more about our motor-starting studies.
Relay Coordination Analysis
Proper application and coordination of over-current relays and other protective devices is vital in a system requiring reliable electrical service. EasyPower expert engineers bring the critical experience needed for the proper application of ANSI and NEC requirements to equipment protection.
In addition to relays that respond to short circuits, low voltage breakers, differential, directional, power, under voltage, out-of-step, and other special protective relays often need to be set. This EasyPower study will include detailed tables listing the recommended settings and discussion of any limitations.
Contact us to learn more about EasyPower relay coordination studies.
The increasingly widespread application of SCR-controlled drives in industrial processes has brought harmonic consideration into the design of electrical systems. It is common practice for industrial plants with major harmonic sources to add harmonic filters to limit voltage distortion and harmonic current flows into the utility system. On existing systems, harmonic measurements are usually made to determine the extent of voltage and current distortion and are used as a base for further calculations. If calculations show that harmonic filters are required to meet specified criteria, filters can be designed and analytically tested.
Harmonic filters must be integrated with power factor correction capacitors and must withstand any harmonics absorbed from a utility system or neighboring plant. Filters must also continue to function when loads in the plant vary or major elements such as transformers are taken out of service for maintenance. With careful planning, filters can be designed to reliably serve their intended purpose without creating new problems.
EasyPower’s harmonic analysis will reveal:
- Harmonic current paths
- Amount of harmonic current flowing into the utility system
- Generated harmonic voltages
- Potential resonances
- Performance of filter and capacitor bank tuning options
- Comparison of results against the latest IEEE 519 standard
Contact us to learn more about EasyPower harmonics studies.
System Stability Analysis
The stability of synchronous motors and generators has long been a design consideration in industrial and co-generation plants, as well as utility systems. It is necessary to ensure the network, synchronous machines, and protective systems will function adequately so faults do not interrupt operation.
Where instability is shown to be a potential problem, several practical alternatives can usually be used to eliminate the source of the problem. In some situations, changes to the network can improve stability; while in others, protective systems can be installed to avoid machine damage and minimize the disturbance.
An EasyPower system stability study can include:
- Induction generator over-excitation from capacitors
- Induction motor low- and high-voltage effects
- Motor transfer analysis when switching sources
- Reaccelerating analysis to guide plant operators
- Impact loading on motor shafts
- Emergency generator performance applied to load recovery
- General system stability
One form of output from a dynamic study is graphical time response or impedance plots. These plots can show variations in voltage, machine angle, frequency, line flows, and apparent impedance.
Contact us to learn more about EasyPower stability studies.
Load Shedding Analysis
Load shedding is a special form of dynamic study most frequently associated with electrical systems having in-plant generation. The time period of examination is usually longer due to the slower response of governors. Loss of a major source, usually the utility, can have a severe effect on plant voltage and frequency. Rapid corrective action may be required.
An EasyPower load shedding study can help determine if standard load shedding relays are adequate or if a computer-based load shedding system is required. EasyPower engineers examine different operating scenarios to determine the speed and amount of load to be shed for successful recovery, while keeping critical loads through a disturbance.
Contact us to learn more about EasyPower load shedding studies.